The Reflex 6" Class 1 Insulated Flue Pipe is a twin wall prefabricated insulated chimney manufactured from stainless steel; with a 25mm cavitiy.
The system is suitable for use on oil, gas, wood and solid fuel appliances except condensing boilers. The system consists of straight lengths and associated fittings and is available in 125mm, 150mm, 180mm and 200mm diameters.
The Reflex 6" Class 1 Insulated Flue Pipe has 25mm Ceramic Mat insulation with a 316 stainless steel inner liner and a 304 outer stainless steel wall. The liner seam of both inner and outer are continuously welded. The components are assembled by male and female coupler and 1/8 the turn to lock the items together on the serrated coupler. The system is the locked securely with a locking band. The DS system is manufactured under ISO9001 and has been tested to BSEN 1856 – 1: 2003 and in accordance with general requirements of BSEN 1443:2003.The Ventilated Fire stop arrangement has been tested to comply with BS 476: Part 20:1987.
The Reflex 6" Class 1 Insulated Flue Pipe is suitable for use both internally and externally on the following appliances:
• Solid Fuel appliance
• Wood burning Stoves
• Atmospheric gas appliance
• Natural draft oil fired appliances
• The Reflex 6" Class 1 Insulated Flue Pipe is not suitable for use on condensing appliances.
Installation must be in accordance with local and national building regulations. The installation of a flue or chimney should be carried out by a competent person. They may connect to an appliance that is not connected to the fuel supply. The connection of an appliance that is connected to the fuel supply must be carried out by an approved Gas Safe (previously CORGI) for gas fueled appliances, OFTEC installer for oil and HETAS for solid fuel. The Building Regulations Document J (in England, Wales & Northern Ireland) covers the suggested installation of chimneys and flues. The installation must also comply with BS7566 pts 1,2,3,4 for oil flues and BS5440 pt 1: 2000 for gas flues up to70kw.
All components are joined together with a twist lock end cap this requires a 1/8 the turn to lock the components. The joint is then locked using a locking band that is designed to cover the joint of the two components and snap shut. The male end should be the uppermost and pointing in the direction of the flow of the gases produced. Joints should not be made within wall and ceiling spaces. Connecting pipes should be connected to the chimney in accordance to the recommendations of Building Document J.
Reflex 6" Class 1 Insulated Flue Pipe (200mm)
- Product Code: FP0003
- Availability: In Stock